o OMNIVS1500XL (some warnings)
If you have used Tripp Lites PowerAlert software to connect to your UPS, there is a good chance that tripplite_usb will work if it uses one of the following protocols:
o Protocol 0004
o Protocol 1001
o Protocol 2001
o Protocol 3003
On the other hand, if the web page for your UPS on the Tripp-Lite website says "HID-compliant USB port also enables direct integration with built-in power management and auto-shutdown features of Windows and MAC OS X", then you should use the usbhid-ups(8) driver instead.
This driver supports the following optional settings in the ups.conf(5) file (or with -x on the command line):
offdelayThis setting controls the delay between receiving the "kill" command (-k) and actually cutting power to the computer.
battery_min, battery_maxThese floating-point values correspond to the "empty" (10%) and "full" (100%) voltages of the battery. They are used for an approximation of the battery state-of-charge. The calculated battery.charge value will be clamped to the range of 10% through 100%, so the resting voltage of the charged battery can be used for battery_max, and the higher float charge voltage should not cause problems.
busThis regular expression is used to match the USB bus (as seen in /proc/bus/usb/devices or lsusb(8); including leading zeroes).
productA regular expression to match the product string for the UPS. This would be useful if you have two different Tripp Lite UPS models connected to the system, and you want to be sure that you shut them down in the correct order.
This regex is matched against the full USB product string as seen in lsusb(8). The ups.model in the upsc(1) output only lists the name after TRIPP LITE, so to match a SMART2200RMXL2U, you could use the regex .*SMART2200.*.
productidThe productid is a regular expression which matches the UPS PID as four hexadecimal digits. So far, the only devices that work with this driver have PID 0001.
serialIt does not appear that these particular Tripp Lite UPSes use the iSerial descriptor field to return a serial number. However, in case your unit does, you may specify it here.
For more information on regular expressions, see regex(7)
ups.delay.shutdownThis variable is the same as the offdelay setting, but it can be changed at runtime by upsrw(8).
ups.idSome SMARTPRO models feature an ID that can be set and retrieved. If your UPS supports this feature, this variable will be listed in the output of upsrw(8).
outlet.1.switchSome Tripp Lite units have a switchable outlet (usually outlet #1) which can be turned on and off by writing 1 or 0, respectively, to outlet.1.switch with upsrw(8). If your unit has multiple switchable outlets, substitute the outlet number for 1 in the variable name. Be sure to test this first - there is no other way to be certain that the number used by the driver matches the label on the unit.
The driver was not developed with any official documentation from Tripp Lite, so certain events may confuse the driver. If you observe any strange behavior, please re-run the driver with -DDD to increase the verbosity.
So far, the Tripp Lite UPSes do not seem to have a serial number or other globally unique identifier accessible through USB. Thus, when monitoring several Tripp Lite USB UPSes, you should use either the bus or product configuration options to uniquely specify which UPS a given driver instance should control.
For instance, you can easily monitor an OMNIVS1000 and a SMART1500RM2U at the same time, since they have different USB Product ID strings. If you have two SMART1500RM2U units, you would have to find which USB bus number each unit is on (via lsusb(8)), which may result in ambiguities if the available USB ports are on the same bus.
Some of the SMART*2U models have an ID number, but because this ID is not exposed as a USB string descriptor, there is no easy way to use this ID to distinguish between multiple UPS units on a single machine. The UPS would need to be claimed by the driver in order to read this ID.
Written by Charles Lepple, based on the tripplite(8) driver by Rickard E. (Rik) Faith and Nicholas Kain. Please do not email the authors directly - use the nut-upsdev mailing list.
A Tripp Lite OMNIVS1000 was graciously donated to the NUT project by Bradley Feldman (http://www.bradleyloritheo.com)
tripplite(8), tripplitesu(8), usbhid-ups(8)
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/
|Network UPS Tools 2&.7&.3&.||TRIPPLITE_USB (8)||12/29/2015|